The study revealed that only 25 percent of the sidelighting photocontrol systems in the studied buildings were functioning well, whereas almost 100 percent of the toplighting photocontrol systems were found to be functioning well in the previous study. What went wrong?
In this special report by the Lighting Controls Association, we will describe bi-level switching code requirements, its role in the Commercial Buildings Deduction, methods and equipment, and the results of a study of typical energy savings achievable with bi-level switching in popular applications.
Dimming of fluorescent lighting offers significant benefits in terms of supporting visual needs with good lighting, giving users control of their own lighting, and energy savings. The advent of digital dimming offers a new option with clear advantages over traditional analog dimming. Digital dimming can be used almost anywhere that analog dimming can be used, for the same purposes: visual needs, personal control, daylight harvesting, scheduling and other control strategies. If fluorescent dimming is desirable for a given application, digital dimming can offer distinct advantages related to intelligence, flexibility and two-way communication.
While today’s occupancy sensors offer robust features, proven utility and reliability, they remain application-sensitive devices, which requires a properly educated designer and installer for the controls to be effective. The right occupancy sensor must be selected, it must be properly located and installed, and it must be field-calibrated.
In this article, we will examine the seven steps of the effective application of occupancy sensors.
The Weidt Group conducted a study of daylight harvesting projects to find out if daylight harvesting projects are living up to their expectations. The team—consisting of Eijadi, Prasad Vaidya, Tom McDougall, Jason Steinbock and Jim Douglas—reviewed dozens of completed projects, most of which were sidelit using windows, and separated the success stories—some of them operating for 25 years—from projects they considered to be failures.
Automated lighting control—programmable dimming and on-off control—can transform a home as well as the homeowner’s lifestyle. With declining costs and complexity, these systems are no longer exclusively the province of luxury homes.
Indoor spaces with high ceilings, such as factories, warehouses, big box retail stores, gymnasiums and all-purpose rooms are often lighted by probe-start metal halide lighting systems. At higher ceiling heights, 350W and 400W units are common …
Advancements in lamp and ballast technology have resulted in two alternatives to this basic system that can significantly reduce energy consumption while providing other benefits. The first alternative is fluorescent T8 or T5HO hi-bay fixtures, which can replace probe-start metal halide fixtures in retrofit or new construction for energy savings up to about 50%. The second alternative is pulse-start metal halide lamp-ballast systems, which can provide up to 25% energy cost savings in existing applications and up to 30% in capital and operating costs in new construction.
A number of studies demonstrate that personal dimming can result in higher productivity—specifically in the metrics of vigilance, motivation and satisfaction—and also in energy savings. This dual impact can result in an improved bottom line and more satisfied employees and tenants. These advantages are resulting in a significant new trend towards adoption of personal dimming solutions among designers and building owners.
This white paper makes the case for personal control, in particular giving occupants the ability to control their own light levels through dimming.